Soakaway problems and their causes solved by Homeseptic.
We offer a FREE quotation for any Septic Soakaway or Drainage field Installation, repair or replacement in the UK. Get in touch to arrange or just to talk through your problems. Call us on 0800 3101092 or via our contact form
Soakaway & Drainage field Problems and their causes
What is the difference between a Septic Tank and a Soakaway?
A Soakaway is used in a Septic Tank or Sewerage Treatment Plant system when the discharge from your tank is not emitted directly to a watercourse.
In a Septic Tank system a Soakaway if correctly installed treats the sewerage. The Septic tank is a separation device holding the most offensive pollutants. A Soakaway does not need to be emptied a Septic tank does.
What is the function of a Soakaway?
The function of a soakaway, when coupled with a Septic Tank, is to treat the separated waste from the tank and discharge the treated liquid over a wide area to avoid flooding and effectively a soggy garden.
When used with a Sewerage Treatment Plant the function or job of a soakaway is different. Its job is to primarily distribute the treated output of the tank. This will prevent any areas of soggy or waterlogged garden.
How do you know if your soakaway is having problems?
The main problem with a soakaway is that they can become blocked. The blockage can be caused by many factors, which we discuss below. However, when a Soakaway becomes blocked, and it will inevitably at some point, you will certainly know about it. Imagine running a bath and leaving the plugin, this is essentially what will happen. The water and waste will have nowhere to go and so will back up. The warning signs are many but inevitably take the form of bad odours and or the pooling or collection of water in previously dry areas. You will also likely see baths, toilets and appliances draining less quickly and potentially overflowing. If you have a Septic Tank, Sewerage Treatment Plant or Cesspit in the system they will fill up and overflow.
Soakaway Problems, Failed, Broken or Blocked
A Blocked, Failed or Broken Soakaway or drainage field
The adjacent picture shows the most obvious sign that something is not working with your Soakaway. A big puddle of standing liquid where your drainage field/ Soakaway is. Clearly not much is Soaking away here!
In this particular example, the problem with the Soakaway was a poor installation. Both poorly planned and installed. The main problem being that no account was taken for the winter water table. When the winter rain came the water table rose to the level of the soakaway. This meant there was nowhere for the discharge from the system to go.
There was no way of repairing or replacing the adjacent soakaway in or around its current location. The water table was too high, which a percolation test of the ground conditions would have shown. Clearly, a percolation was not undertaken and waste water was flowing directly into a brook. The owner was lucky that the Environment Agency had not seen what amounted to an open sewer. As you will recall a septic tank does not treat the waste water, so it combined with suspended solids was being emitted. With the upcoming legislation change, 1st Jan 2020, the Environment Agency will have a much stronger mandate.
a sewage treatment plant has an internal treatment system. Therefore, if there is a soakaway failure the problem is not so acute. The Environment Agency, providing the treatment system is well maintained and tested wouldn’t have such a big issue. In a septic tank system, the soakaway is the treatment system.
How do you know if your soakaway has failed?
If your Soakaway has failed then the wastewater will have nowhere to go. The system will quickly fill up and prevent further wastewater from entering the system. If the problem is not fixed any holding point in the system will fill up and overflow. Also inspection chambers, open drain points will overflow. Any additional waste water you attempt to put into the system will have nowhere to go. This will lead to overflowing toilets and drains, broken appliances and some pretty bad smells.
A Soakaway is classified as failed if it cannot be repaired and requires a new installation. Soakaways by virtue of their function and design will eventually fail. Many of the symptoms of a failed Soakaway are similar to a blocked repairable Soakaway. To identify a failed Soakaway we would inspect the current Soakaway and the problems it has. Given our years of experience, we can normally tell pretty quickly if the Soakaway is repairable. To make this call yourself without experience is tough. Check the installed filters to see if they are blocked. Check that the system is discharging to the Soakaway if it is not then the problem is not your Soakaway. Excavate a section of the Soakaway, does water then flow freely into the excavation hole. If it doesn’t then the problem, blockage or failure is likely in the Soakaway system. If the water does flow freely and the soil is black and pungent then failure is likely.
What are the main causes of Soakaway problems?
- Flushing inappropriate things down the toilet – baby wipes, nappies, tampons etc. These items are likely to cause problems before they reach your Soakaway but will obviously cause a blockage. With modern Sewerage Treatment Plants, these items will cause the failure of the tank and are very costly!
- Not regularly emptying your Septic Tank of Sewerage Treatment Plant. While this may initially seem like a money saving idea it will cost you more in the long run.
- Tree and plant roots growing through the pipes of the soakaway or anywhere in the system. This can prevent the wastewater passing through the soakaway. Tree roots are especially harmful.
- Collapsed or displaced pipes in the soakaway. This can be caused by natural movements in the soil or say by driving a heavy car etc over the drainage field.
- Damage to the dip pipes or baffle within a septic tank can cause a soakaway to become blocked.
- Poor maintenance of the Soakaway filters. These will require high-pressure water to clean.
- Failure or problems with your Septic Tank or Sewerage Treatment plant which allow untreated waste to enter the system. With a Septic Tank system, this is less problematic but will cause permanent damage in the long run. Soakaways for Sewerage Treatment plants are not designed to deal with waste.
- The biggest cause by far is an initial poor Installation. The common signs of a poor installation are no filters installed or the Soakaway being too deep. If the Soakaway is too deep then Aerobic digestion and processing will be impossible.
- As well as a poor installation another common problem is poor planning by cowboy firms. Many firms do not carry out proper percolation tests. This means they have no idea how quickly the intended area will drain water. Also if the area is suitable for a Soakaway drainage field at all.